2-23. POWER DISTRIBUTION PANEL (CONT)
Check to see if electrical power to each area of
the laundry is off by momentarily switching ON
the washer, dryer, extractor, etc.
Switch main breaker (2) to ON.
Check to see if electrical power is supplied to
each area of the laundry by momentarily
switching on the washer, dryer, extractor, etc.
Switch each piece of equipment on and off by its
appropriate breaker switch (3), (4), (5), (6), or
High voltage is present on this equipment. Do not perform maintenance with
power on. Death or serious injury may result.
Turn power off at source.
Repair panel box by replacing unserviceable breakers with new breakers of the same value. All circuit breakers
are removed and replaced in similar manner. Only one circuit breaker is covered in these procedures.
Open breaker panel box (8).
Loosen four screws (9) and remove two border panels (10) and two border panels (11).
Remove four screws (12) and face plate (13).