2-25. POWER DISTRIBUTION PANEL (CONT)
W A R N I NG
Check to see if electrical power to each
area of the laundry is off by
momentarily switching ON the
washer, dryer, extractor, etc.
Switch main breaker (2) to ON.
Check to see if electrical power is
supplied to each area of the laundry by
momentarily switching on the washer,
dryer, extractor, etc.
Switch each piece of equipment on and
off by its appropriate breaker switch
(3), (4), (5), (6), or (7).
High voltage is present on this equipment. Do not perform maintenance
with power on. Death or serious injury may result.
1. Turn power off at source.
Repair panel box by replacing unserviceable breakers with new
breakers of the same value. All circuit breakers are removed and
replaced in similar manner.
Only one circuit breaker is covered in
Open breaker panel box (8).
Remove four screws (9) and remove two border panels (12) and two border panels (13).
Remove four screws (11) and face place (10).