This equipment operates at High Voltages. Use extreme caution.
Disconnect power from CSSL before proceeding with the following
procedures. Touching a live wire can cause serious injury or death.
This procedure requires two MOS 51R, 52C, 52D, or 52G.qualified persons. Switch the main breakers in
power distribution panel #1 and #2 to the OFF position. Shut down power supply. Disconnect 100AMP
power cables from power entry box connector plugs J1 and J2. Disconnect all other power cables
connected to the power entry box.
Remove Connectors and Plugs
Use caution when cutting electrical wires from the connectors or plugs to
prevent injuries from cuts.
Remove power entry box rear cover (1). Remove defective connector by loosening and removing the
retainer ring (reverse thread) (2), securing the connector (3) to the power entry box sleeve. Pull connector
out of sleeve. Cut wires (4) as close to the defective connector (3) as possible. Tag wires. To remove the
GFCI receptacle (5), remove the hex nuts holding the receptacle and cover (6) to the entry panel. Push
the receptacle and cover out to remove it. Retain the cover.