TM 10-3510-223-13&P 0005 00
PREPARE POWER DISTRIBUTION SYSTEM FOR USE
This procedure must be performed by civilian personnel (electrician), or qualified military personnel with
MOS 51R, 52C, 52D, or 52G.
The CSSL modified cargo container must be electrically grounded.
Failure to ground the CSSL may result in serious injury or death from
If ungrounded power will be used to operate the CSSL, the container must be grounded as follows:
Drive grounding rod (1) 8 into the ground near the power entry panel (2).
Back off hex nut (3) on grounding terminal (4) to expose the eye (5).
Insert ground cable (6) through eye (5) and tighten hex nut (3).
Ensure cable (6) is securely attached to grounding rod (1). Tighten setscrews (7) if necessary.