TM 10-3510-223-13&P 0005 00
Qualified civilian personnel (electrician) or military personnel in MOS 51R, 52C, 52D, or 52G are required
to connect the 100AMP power cables.
Ensure all circuit breakers on circuit breaker panels #1 and #2 are set to
OFF to prevent shorting of equipment when power is initially connected.
Connect 100 AMP, 50 ft cables (1) to power input plug J1 (2) and J2 (3) on the power entrance box (4).
Have qualified personnel, as noted above, connect pigtail end of 100 AMP, 50 ft cables (1) to the power
source (e.g., generator, municipal power supply, etc.).
If TEMPER interior lights (6) are used, lay out and connect 120VAC extension cord (5) (in footlocker) to
GFCI receptacle J3 (7) on the power entrance box (4). Turn ON power at the source.
Switch main breakers in Power Distribution Panel #1 and #2 Circuit Breaker to ON. Observe phase
indicator light on Panel #1. When indicator light is on, switch circuit breakers #1 and #29 on Panel #1, and
circuit breaker #3 on Panel #2 (if needed) to ON. To operate the interior lights, turn the LIGHTS switch on
the roadside raceway to ON.