TM 10-3510-223-13&P 0005 00
After the power and freshwater supply connections are complete, and a wastewater collection/disposal
site is connected, the CSSL can be operated. To use the interior lights, turn the LIGHTS switch on the
roadside raceway to ON.
In Power Distribution Panel No.1, set circuit breakers # 2, 9, 10, 15, 16, 19, 22, and 23 to ON
In Power Distribution Panel No.2, set circuit breakers #15, 19, and 23 to ON.
The freshwater pump is not used when the CSSL is connected to a
municipal water system that supplies sufficient water pressure. Water
supply is then regulated with the gate valve located behind the
freshwater panel. However, when a static supply, such as a 3,000 Gallon
fabric tank is connected, the freshwater pump must be used to provide
To operate the CSSL with a static water supply using the water pump (1), the Set circuit breaker #28 on
Power Distribution Panel #1 to ON.
Ensure that pump drain valve (2) is closed.
Attach garden hose to the hose fitting at the end of the freshwater line (3), located behind washer/dryer
#6 and open the gate valve (4).
Turn the switch marked FRESH WATER PUMP on the roadside raceway (5) to ON.
Start the pump by lifting the lever (6) on the side of pressure switch to override the shutoff. Hold lever until
the pressure gage (7) indicates 20 lbs of pressure, then release lever.
When water flows from the garden hose attached to the end of the freshwater line, close the gate valve
After the pressure switch lever (6) is released, the pressure tank (8) regulates the operation of the pump
in accordance with the needs of the wash system.
If pressure gage shows no pressure after pump has run for several minutes, refer to Unit Maintenance.