TM 10-3510-223-13&P 0005 00
CSSL TEMPORARY SHUTDOWN
If the CSSL will not be needed for an extended period, it should be shut down temporarily.
If the CSSL needs to be shut down because of unusual weather
conditions, refer to work package 0006 00.
The CSSL components are heavy. To avoid injuries, four persons are
required to perform this procedure.
To shut down the facility while it remains in place proceed as follows:
Ensure washer/dryers have completed their cycle.
When municipal water is used:
Shut off the fresh water supply at the source. Disconnect garden hose (1) from the source and the fitting
on the freshwater panel (2) on the curbside of the container.
Connect the garden hose (1) to the threaded fitting (3) at the end of the supply line and open the gate
valve (4) to let the system drain.
After supply line has drained, disconnect hose (1). Drain the hose, coil it, and set aside. Close gate valve
(4) after system has drained. Close gate valve (5) inside the freshwater inlet panel.