TM 10-3510-223-13&P 0005 00
PREPARE POWER DISTRIBUTION SYSTEM FOR SHIPMENT
Power source must be shut down/secured before disassembling any
cables to prevent electrical shock.
This procedure can only be performed by qualified civilian or military
personnel in MOS 51R, 52C, 52D, or 52G.
Set all individual and then the main circuit breakers on power distribution panels #1 (1) and #2 (2) to
OFF. Turn power source OFF.
Disconnect 100 AMP Supply Cables (3) from J1 and J2 Connectors on the power entry box (4) and from
power source (5).
Disconnect power cables from J3 (6) and J4 (7) Connectors on the power entry box (4).
Install dust covers on all power input box connectors and 100 AMP Supply Cables (3). Coil the Cables.
Disconnect ground wire (8) from ground terminal on power entry box (4).
Recover ground rod, disassemble and clean.