Table 1. Preventive Maintenance Checks and Services for the CSSL-Continued.
Item to be
Equipment not ready/available if:
Check Modified End Section (15) for rips,
tears, missing hardware or improper
Ripped or torn fabric. End wall not properly
Do not touch damaged circuit breakers.
Notify Direct Support Maintenance.
Open circuit breaker panel (17) and
examine circuit breakers. Note any
damage to the breakers or to the panel. If
no damage is noted, activate the
breakers to determine their proper
Damaged or non-functioning
With the main circuit breaker (#10) in the
left side power distribution panel set to
ON, set circuit breaker #17 to ON and
test the GFCI receptacle on the power
entry panel in the utility wall (18) by
pushing the TEST button. Observe the
indicator light. If the indicator light does
not activate, push the RESET button.
Repeat the test. If the receptacle does not
work, refer to Unit Maintenance.
Receptacle does not work, is damaged or is
Open washers (1) to determine if the
water has not drained properly, any
clothes or other items. Drain water by
activating the washer. (if water remains,
notify Unit Maintenance). Check the
condition and proper attachment of the
freshwater (2) and wastewater (3) hoses.
Check for leaks. Check and, clean out the
dryer lint traps (4). Check for secure
attachment and general condition of the
dryer exhaust ducts (5).
Washers leak, drain line clogged, filters
clogged, water lines loose damaged corroded
If light (8) fails during operation, replace
the light bulb (refer to WP 00015 00). If
light fails to operate, notify Unit
Light fixtures or light switch inoperative.
Excessive number of light bulbs burned out.