Using a 3,000 Gallon freshwater tank:
1. Shut off the freshwater pump (1) by setting circuit breaker #3 in the Right Side Power Distribution Panel to OFF.
Disconnect the 2 freshwater hose (2) from the freshwater inlet panel (3) on the utility wall. Hold the end of the hose
above the water level in the freshwater tank (4) and place the end of the hose (2) into the freshwater tank as shown.
Install dust cap (5) on panel (3).
2. Connect garden hose to the hose fitting (6) located at the end of the supply line (behind washer/dryer #6) and
open (handle in line with water line) the ball valve (7) to let the system drain.
The 3,000 Gallon water tank is heavy. To avoid injuries, four persons are required to
prepare the CSSL for shipment.
3. Drain the 3,000 Gallon freshwater tank (4) in accordance with TM 5-5430-237-12&P. Remove the 2 freshwater
hose (2) from the freshwater tank (4). Drain the hose, coil, and set aside. Disassemble and place 3,000 Gallon
freshwater tank (4) into cover in accordance with TM 5-5430-237-12&P.
4. After water line has drained, disconnect garden hose from the hose fitting (6). Leave ball valve (7) in open (handle
in line with water line) position after system has drained. Drain the hose, coil it, connect the ends together and set it