THEORY OF OPERATION-CONTINUED
Electrical System Washer Side
The CBL receives 208 VAC power from a 100kW generator or approved municipal power source through
three 100A cables. One cable feeds the power service panel at the washer end (Figure 7, Item 1) of the
container. The power service panel (Figure 7, Item 2) at the washer end of the container distributes
power to the main circuit breaker panel (Figure 7, Item 3). Power is then distributed through circuit
breakers to the washers, exhaust fans, CBL lighting, and filtration system pumps. Service outlet
receptacles (Figure 7, Item 4) that are GFCI protected are located at each end of the container and at
the center for powering work lights and other external components. A 60A outlet (Figure 7, Item 5) is
provided for powering the FDECU or ASH. All outlet receptacles are controlled and protected by the main
circuit breaker panel.
Figure 7. Electrical System.