Table 1. Plumbing Troubleshooting Procedure for Containerized Batch Laundry Continued.
TEST OR INSPECTION
Refill water supply. Ensure CBL
6. Pump P-1 short cycles
Verify water supply and valve setup.
is set up IAW TM 10-3510-226-
Repair leaks in hoses, pipes, or
Inspect system for leakage.
Water Treatment System
Adjust pressure switch IAW
Check pressure switch (Figure 9, Item
1) settings. Ensure pump activates at
30 psi and shuts down at 60 psi.
Ensure check valve (Figure 10, Item
Service or replace check valve
2) is operable.
If further corrective action is
required, notify direct support
Figure 9. Pump P-1 Short Cycles Pressure Switch.