BOILER TROUBLESHOOTING PROCEDURES-CONTINUED
Table 1. Boiler Troubleshooting Procedures for Containerized Batch Laundry Continued.
TEST OR INSPECTION
Provide sufficient fuel of the
Ensure fuel supply (Figure 3, Item 1)
3. Excessive fuel
correct type (JP-8, DF-1 or DF-
is of sufficient quality and quantity, and
2). Bleed fuel system IAW WP
fuel system has been bled.
bleed, inspect and replace fuel
filter IAW 10-3510-226-10 as
Fuel consumption will
increase if operating
Shut down CBL operation
Check for fuel leakage. Ensure hoses
immediately and remedy source
are connected correctly to the fuel
Use a screwdriver in the
Check temperature settings on the
adjustment hole (Figure 3, Item
operating thermostat (Figure 3, Item
3) to reset thermostat settings to
205 oF 210 oF in the
temperature dial window (Figure
3, Item 4).
Verify operation of draft inducer fan
Replace inoperative draft
Check burner air intake (Figure 3,
Clear burner air intake of dirt
and lint. Ensure damper
adjustment is tight. Check
Inspect fuel nozzle (Figure 3, Item 7).
Tighten or replace fuel nozzle
Check exhaust gas sensor (air switch)
(Figure 3, Item 8).
If further corrective action is
required, notify direct support