Clean the Fuel Pump Strainer
Ensure fuel is contained and not allowed to spill or spray into the CBL. Failure to observe
safety precautions may result in a fire, with the possibility of serious injury or death to
Disconnect power by switching the circuit breaker to off.
Loosen the two compression nuts retaining the fuel pipe to the burner and remove the fuel pipe.
Remove the screws retaining the pump cover (Figure 7, Item 18) and remove the pump cover.
Remove the pump strainer (Figure 7, Item 19) and rinse in clean fuel.
Install strainer (Figure 7, Item 19).
Ensure pump cover gasket is in place and install pump cover (Figure 7, Item 18). Retain with
Install fuel pipe and tighten compression fittings.
Connect power, and operate IAW procedures given in TM 10-3510-226-10.
Monitor for normal operation.
Figure 7. Clean the Fuel Pump Strainer.