Adjust the High Temperature Cutout
Ensure that all electrical power to the boiler is shut off and disconnected before
proceeding. The circuit breaker box or individual circuit breaker should be locked and
tagged out by personnel following this procedure. Remember that the CBL is a wet
environment. Serious injury or death to personnel can result from electrocution if proper
safety precautions are not observed.
Allow the boiler and any associated hot water pipe, tubing or fixtures to cool at least 30
minutes before attempting any repairs. Failure to observe safety precautions may result
in serious injury or death to personnel.
1. Switch the boiler off at circuit breaker No. 22, and allow the boiler to cool for at least 30 minutes
2. Ensure the dial (Figure 10, Item 10) has been set for approximately 210 oF.
3. Switch the boiler on at circuit breaker No. 22, and operate the boiler for at least 30 minutes IAW
procedures given in TM 10-3510-226-10.
4. Monitor for normal operation.