15. Install the coolant reservoir IAW procedures given in WP 0073 00.
Antifreeze used in the following procedure is highly toxic. Wear appropriate protective
clothing when handling antifreeze/glycol. If antifreeze contacts eyes or skin, flush the
affected area immediately with clean water and seek medical attention.
Do not make substitutions for the antifreeze. The use of antifreeze other than the type
identified in the Expendable and Durable List may decrease performance. Failure to
comply may shorten the life span of the equipment.
16. Refill system with ethylene glycol, and connect power IAW TM 10-3510-226-10.
17. Monitor for normal operation.
Figure 2. Replace the Circulation Pump.
END OF WORK PACKAGE