4-60. DISTRIBUTION BOX MAINTENANCE - continued.
Inspect for broken wires, cracked or frayed insulation, and burnt or charred insulation.
Inspect distribution boxes for cracks, dents, holes, corrosion, and signs of burning or charring.
Inspect cover for missing, broken or misaligned flip top covers.
Inspect all parts for proper connection.
Repair. Repair is limited to the replacement of defective parts and the following:
Lug Terminal Replacement.
Crimp lug terminal (1) on both ends of the white/green wire (2).
Replace lug terminal (3) on the green wire on the cable (4).