TM 10-3510-223-13&P 0019 00
CONTAINERIZED SELF SERVICE LAUNDRY (CSSL) MODEL A
0019 00-1/(2 Blank)
THIS SECTION COVERS:
CSSL in operation
Tools and Special Tools
Tool Kit General Mechanic (WP 0045, Table 2, Item 1)
Inspect the pressure switch (1) and gage (2) for damage. Check for legibility of scale, internal corrosion,
and leaks. Observe proper functioning of pressure switch and gage during normal operation of facility.
The pressure gage should move between 15 and 30 PSI during normal operation. The water pump (3)
should start when the pressure reaches 15 PSI and turn off at 30 PSI. Refer an inoperable pressure
switch or gage to direct support maintenance.
END OF WORK PACKAGE