SHOWER, ENCLOSED UNIT, SYSTEM
SUMP PUMP TANK
Shop Equipment Automotive Maintenance and
Repair: Organizational Maintenance, Common
Containerized Shower / Shower, Enclosed Unit,
System set up.
Clean the Graywater Holding Tank
When the shower is in operation on a more or less daily basis, the graywater tank must
be cleaned approximately every 30 days. To prepare the tank for cleaning requires two
persons. The graywater tank on the Containerized Shower may be easier to access by
opening the service doors. The Shower, Enclosed Unit, System, does not have service
doors, and must be accessed from the interior of the shower.
1. Remove the screws (1) securing the equipment mounting platform (2) and the padeyes (3) to the
mounting rails (4) (Containerized Shower only).
The equipment mounting platform is heavy, awkward, and difficult to maneuver. Wear
protective gloves before handling. To prevent injury, two persons are required to remove
and carry it. Failure to observe safety precautions may result in serious injury to
The equipment mounting platform has sharp edges or corners. Wear protective gloves
before handling. Failure to observe safety precautions may result in serious injury to
2. Lift the equipment mounting platform (2) and place it outside the shower container (Containerized
3. Remove the bolts securing the graywater tank cover plates (5) and duct cover plates (6) in place, and
remove the plates.